Posted by | 12 January 2017
Many supposedly accessible toilets neither comply with the guidance in Doc M, nor do they meet British Standard BS 8300-2009. Some are just difficult to use but some are actually quite dangerous.
As an able-bodied person, it may be difficult to appreciate exactly why some of the features provided in an accessible toilet are required and how important their positioning is.
Here we provide an explanation of some of the issues to give you an idea why Doc M is so important.
To fully understand the importance of the requirements, you must put yourself in the position of a disabled person and consider the following points…
The seat of a standard wheelchair is approximately 480mm above floor level. Standard toilet pans are around 430mm to the top of the seat. It may be possible to slide off the wheelchair and drop onto the toilet seat. Getting back onto the wheelchair is a different matter. Even with good upper body strength, it is practically impossible for most people to raise themselves up by around 50mm and across by 600mm using arm strength alone. The likelihood is that, having reached the toilet, you will be fully committed to using it so you go ahead and transfer from your wheelchair to the WC. You are then faced with a couple of possibilities, neither of them attractive.
Some disabled people need to wash their hands first before rearranging their clothing and transferring back to their wheelchair. To find out for yourself how important the position of the basin is, whilst sitting on a chair, lift your legs off the ground, stretch your arms out in front of you and see how far you can reach forward without losing your balance. You will find it is not very far.
It is also important to note the correct positioning of a basin with the tap fitted on the corner nearest the WC. This helps people who may need to rinse out a bottle or container which would be impossible if the tap was centralised.
The flush lever should be on the open side of the cistern (not on the wall side). You should be able to flush it using a hand, an elbow, or any other part of the body. Some people do it with their chin. If it is not on the open side, it will be impossible to reach from a wheelchair.
The fold down rail should be easy to pull down and push up from a seated position. The rails used should contrast with the surrounding walls to assist those with visual impairments.
When you look at the reasons behind the regulations, it all becomes obvious. Imagine the difference you could make to someone’s life by installing a Doc M compliant toilet or shower facility correctly and showing an understanding of the need for the product to your customer. Would you want to face a non-compliant disabled toilet?
Doc M packs range from toilets, shower & changing rooms. They all offer the user a level independence giving that person a greater sense of self.
You can speak to one of our team for any advice or guidance on Doc M by calling us on 01642 710719 or email firstname.lastname@example.org
Ref: Information extracted from original article by David Spooner, an independent access and product design consultant. Click here for original document
We have a team of experts specialising in all aspects of inclusive washroom equipment. If you need a comprehensive range, we do it all - and it is all we do!Find out more
NYMAS Doc M Packs contain all the sanitaryware and fittings to comply with the standards set out in Doc M. They have been approved by LABC to meet local authority requirements. NYMAS only use WRAS approved cistern fittings and brassware, and take great pride in the knowledge that we will only supply approved, quality products to the market.Find out more
Accessible equipment distributor
© Copyright Nymas 2016. All rights reserved. Built by r//evolution.